Equivalent Length Method
The equivalent length method (The Le/D method) allows the user to describe the pressure loss through an elbow or a fitting as a length of straight pipe.
This method is based on the observation that the major losses are also proportional to the velocity head (v2/2g).
The Le/D method simply increases the multiplying factor in the Darcy-Weisbach equation (i.e. ƒ.L/D) by a length of straight pipe (i.e. Le) which would give rise to a pressure loss equivalent to the losses in the fittings, hence the name “equivalent length”. The multiplying factor therefore becomes ƒ(L+Le)/D and the equation for calculation of pressure loss of the system is therefore:
All fittings, elbows, tees, can be summed up to make one total length, and the pressure loss calculated from this length. It has been found experimentally that if the equivalent lengths for a range of sizes of a given type of fitting are divided by the diameters of the fittings then an almost constant ratio (i.e. Le/D) is obtained. The advantage of the equivalent length method is that a single data value is sufficient to cover all sizes of that fitting and therefore the tabulation of equivalent length data is relatively easy. Some typical equivalent lengths are shown in the table.
- Head loss of hydraulic system is divided into two main categories:
- A special form of Darcy’s equation can be used to calculate minor losses.
- The minor losses are roughly proportional to the square of the flow rate and therefore they can be easy integrated into the Darcy-Weisbach equation through resistance coefficient K.
- As a local pressure loss fluid acceleration in a heated channel can be also considered.
There are following methods:
- Equivalent length method
- K-method (resistance coeff. method)
Why the head loss is very important?
As can be seen from the picture, the head loss is forms key characteristic of any hydraulic system. In systems, in which some certain flowrate must be maintained (e.g. to provide sufficient cooling or heat transfer from a reactor core), the equilibrium of the head loss and the head added by a pump determines the flowrate through the system.