Reactor Pressure Vessel
The reactor pressure vessel is the pressure vessel containing the reactor core and other key reactor internals. Most of commercial power reactors are light water reactors (PWRs and BWRs), which are cooled and moderated by high-pressure liquid water (e.g. 16MPa in case of PWRs) and therefore the reactor vessel must withstand high pressures.
It is a cylindrical vessel with a hemispherical bottom head and a flanged and gasketed upper head. The bottom head is welded to the cylindrical shell while the top head is bolted to the cylindrical shell via the flanges. The top head is removable to allow for the refueling of the reactor during planned outages.
There is one inlet (or cold leg) nozzle and one outlet (or hot leg) nozzle for each reactor coolant system loop. The reactor coolant enters the reactor vessel at the inlet nozzle and exits the reactor at the upper internals region, where it is routed out the outlet nozzle into the hot leg of primary circuit and goes on to the steam generator. The primary circuit of typical PWR is divided into 4 independent loops (piping diameter ~ 800mm), each loop comprises a steam generator and one main coolant pump, but can differ according to certain reactor design. Therefore numerous inlet and outlet nozzles, as well as control rod drive tubes (in case of BWRs) and instrumentation and safety injection nozzles penetrate the cylindrical shell. This number of inlet and outlet nozzles is a function of the number of loops.
The flow path for the reactor coolant through the reactor vessel would be:
- The coolant enters the reactor vessel at the inlet nozzle and hits against the core barrel.
- The core barrel forces the water to flow downward in the space between the reactor vessel wall and the core barrel, this space is usually known as the downcomer.
- From the bottom of the pressure vessel, the flow is reversed up through the core in order to pass through the fuel assemblies, where the coolant temperature increases as it passes through the fuel rods.
- Finally the hotter reactor coolant enters the upper internals region, where it is routed out the outlet nozzle into the hot legs of primary circuit and goes on to the steam generators
The body of the reactor vessel is constructed of a high-quality low-alloy carbon steel, and all surfaces that come into contact with reactor coolant are clad with a minimum of about 3 to 10 mm of austenitic stainless steel in order to minimize corrosion.
The reactor pressure vessels are the highest priority key components in nuclear power plants. The reactor pressure vessel houses the reactor core and because of its function it has direct safety significance. During the operation of a nuclear power plant, the material of the reactor pressure vessel is exposed to neutron radiation (especially to fast neutrons), which results in localized embrittlement of the steel and welds in the area of the reactor core. In order to minimize such material degradation radial neutron reflectors are installed around the reactor core. There are two basic types of neutron reflectors, the core baffle and the heavy reflector. Due to higher atomic number density heavy reflectors reduce neutron leakage (especially of fast neutrons) from the core more efficiently than core baffle. Since the reactor pressure vessel is considered irreplaceable, these ageing effects of the RPV have the potential to be life-limiting conditions for a nuclear power plant.