Rod Drop Method
The rod drop method belongs to a group of reactivity perturbation methods. This method is based on the study of the transient response of the reactor to a rapid insertion of high negative reactivity. This rapid reactivity insertion is usually performed by the dropping of the reactor control rods when the reactor is in a critical state. In this case the reactivity inserted can be determined from the measurement of the prompt drop.
As was described in the Prompt Jump Approximation, the response of a neutron detector (n1 ➝ n2) immediately after a control rod is dropped into a critical reactor (ρ1 = 0) is related by:
which allows determination of the reactivity worth of the rod. The rod drop method is advantageous because it is very quick to perform and it requires no extra equipment. Moreover it can easily and safely measure large amounts of reactivity. On the other hand the rod drop method is associated usually with reactor shutdown and subsequent reactor startup. Also, the rod drop time is not instantaneous as is theoretically assumed, therefore limiting the accuracy of the method. In PWRs, the drop time of all control rods is usually about 2 – 4 seconds.
This method is widely used to determine the worth of all control rods (i.e. of an emergency shutdown system). This method can be also used to determine the parameters of delayed neutrons. These data can be obtained by decomposition of neutron flux coastdown.
A more accurate method is, for example, in:
Moore, K. V. Shutdown Reactivity by the Modified Rod Drop Method, USAEC Report ID0-16948, 1964.